Water heater sediment and limescale build-up - troubleshooting guide and preventing tips. What causes sedimentation, symptoms and how to fix the problem. Is flushing enough? Find out how water heaters, when free of mineral deposits, perform better, have higher efficiency, save on energy and last longer.
Water heater sediments are tiny solid particles coming from the sand, clay or any other debris and since they don’t dissolve in water, they settle at the bottom of the water heater. Sediment build from minerals are present in any water type, either municipal or well.
Mineral deposits such as the limescale are also found on dishes, sinks, and bathtubs. This problem is present, more or less, in any home.
One of the main reasons for the sediment build-up is the hard water, which is rich in minerals, such as calcium and magnesium. This “problem” does not represent a health hazard, but it can severely affect your heater if accumulated beyond repair. Keep in mind that sediment may contain impurities which could lead to bacteria development.
If the heater is not maintained correctly, regularly and per manufacturer’ instructions, water won’t be heated, and you will not have enough water due to the reduced flow.
In cases where the sedimentation is severe, there will be less room for the water so that you will be running out of hot water fast. The tank in such a case is not worth cleaning, so it is better to buy a new unit.
The temperature of water stored inside the tank, fluctuates from hot to lukewarm, affecting the comfort of a user.
Sediment build-up might cause the relief valve dripping. The solution is to drain a heater, clean and tighten the TPR valve connection. If this cannot help, do not try to repair the valve – this is a safety device, and it must be replaced.
If you haven’t flushed a water heater for a long time, a drain valve can also clog, prevent draining and closing, and resulting in an element leak.
Surfaces that are covered with the limescale and exposed to heat could become hotter than if they were clean. As the gas burner cycles ON and OFF, these surfaces and connections will be exposed to rapid expansion and contraction, which can result in cracks and cause premature failure. Extreme temperature could even damage the tank’s lining.
A presence of water heater sediments can cause changes in water color. Flush the unit periodically as part of the regular maintenance and if necessary, install the filter.
Clean the bottom of the tank and heating elements, as deposits can create an insulating layer between the heat source and water, leading to insufficient supply and slow recovery. Over time, this problem can result in dry-fired heating elements. As the lower heating element cycles more often than the upper element, it collects sediments faster and fails more often. This is why Incoloy elements are what you should buy and install, as they will last longer than the components made of copper.
In tankless heaters, a heat exchanger is small, and water passages are narrow, so if it becomes clogged due to deposits, the water flow gets reduced, resulting in high temperatures, hot spots, and premature element failure. Flushing a tankless requires a pump to circulate the water through the heater. The flushing process is different from the tank-type.
You have several options on how to deal with hard water and sediments.
The softener can help you reduce the deposits, but soft water can affect other elements, such as the anode rod, as it will accelerate the anode consumption. If using the water softener, you should inspect the anode rod more often and replace it when needed.
Installation of the whole house water filtration system is another system that is helpful in reducing mineral deposits that are entering the home plumbing from the municipal water system or wells.
Buy a deliming solution from the manufacturer and treat the affected heater as part of the regular maintenance. Flushing a water heater is probably the most popular choice for cleaning the tank and removing the sediments (if the tank is not affected severely). The idea is to weaken the deposits and flush the buildup out, so the tank and water lines become clean. Vinegar can also be used for cleaning the tank, including soaking the elements.
Water heaters are mostly shipped to its new owners with the thermostat set to 120-125 F. Keep it that way because the higher temperature can cause scalding burns much faster and more minerals can be left behind as sediment buildup. So, the hotter the water is more deposits forms on the elements.
The recommendation is to look for the models that incorporate a system that fights the water heater sediment and lime build-up. The idea is simple. An innovative design of the dip tube ensures that the incoming water makes the turbulent flow inside the tank, which dissolves the calcium compounds or slows down calcification. Different manufacturers have different systems; Bradford White has the HydroJet Total Performance System; AO Smith DynaClean and Rheem have the EverKleen system. All these systems can reduce the sedimentation problems with great success.
Note: When the tank is empty, take the opportunity to check the anode rod, dip tube and T&P valve, clean or replace if needed.
A small amount of mineral deposits at the bottom of the water heater is not dangerous, while larger amounts can cause many problems. If you live in an area with hard water, sediment build-up can accumulate fast and calcify, making it difficult to remove. That is why regular maintenance is recommended.